We have updated the existing GEC CDG11, 21 & 31 (3 secs) relay models and have addded the GEC CDG11, 21 & 31 (1.3 secs) relay models to the library.
We have added the Reyrolle 2TJM70 relay to the Library.
We have added the following Areva overcurrent and earth fault relays to the library: MiCOM P126 & P127.
We have added the VIP201 relay model and associated it with the SF6 circuit breaker.
We have added the P+B Engineering PBSJ120 relay and CEE relays: ITG7266, ITG7366, ITG7466 & ITG7566 to the Library.
We have added the Terasaki AT20 ACB plus AOR-1BL-GS trip unit and the ABB trip unit: PR112 to the reference library.
We have added the following Dorman Smith E-Frame MCCBs : 1600A, 2000A, 2500A & 3200A, and Teresaki MCCBs : XS400CJ & XS400NJ to the reference library
Text Box moved in Loadflow Excel Report
Version 3.9.3 :
In the "Voltage Profile" Loadflow Excel Report, the position of the text box (which provides general guidance) has been changed for all charts to the bottom-right of the chart rather than the top-right as previously.
The default fault rating for 415 V busbars has been changed from 31 MVA to the more commonly used 36 MVA rating.
The Database Zip facility has been improved and provides a method for you to send your zip archive to any email address, rather than just ERACS.
We have added the range of Siemens Sentron 3WL ACBs to the reference library, including the following trip units: ETU15B, ETU25B & ETU45B.
The Arc Flash Hazard module has been updated in-line with the latest 2012 edition of NFPA 70E Standard for Electrical Safety in the Workplace.
We have added the following Areva MiCOM P124 & P14x relays to the Library.
Ability to view the key library list in more detail
Version 3.9.3 :
The ability to show the library key list view in more detail.
When selected, the following columns are displayed: "Created By", "Date Created", "Modified By" & "Date Modified". The list can be sorted by any of those new columns, by simply left-clicking in the column header. To display these new columns right-click the list view and select "Show Details" from the menu.
The Arc Flash Hazard module has been updated in line with IEEE Std 1584b-2011.
A new option now exists to allow a maximum clearance time of 2 seconds to be employed for all locations in a study (as per section 4.6 paragraph 1).
The units used within the Arc Flash Hazard module for displaying distance-related items have been improved. Metric distances above 100mm will now be displayed in metres and imperial distances over 12 inches will be shown in feet and inches.